ENEL Electrical Substations - DG 10197
Electrical substation certified type "Microbox" ENEL DG10197
The "MICROBOX" is designed to make a connection with the MV network in antenna for low voltage distribution in rural areas and, in the modernization of the plant, instead of the classic transformer pole.
The box allows to contain a transformer having a maximum power of 250 kVA whose MV side will be directly connected in the cable, while the LV side will be connected to the cabinet for switch BT DS 4548 which in turn will be interconnected to the Controller.
The Electrical substation is normally delivered without equipment and fixtures and accessories with the following components:
- door with two doors fiberglass
- two grids fiberglass
- Oil collection container
- panel for the introduction of the foil voltage detector
- cabinets made of fiberglass framework for BT and the Concentrator
The external color of the cabin Electric is green RAL 6005.
- Reference specifications
ENEL DG 10197 Ed.3
- Dimensions (L x P x h)
Cabin: 2.140 x 2.200 x 1.600 mm
Cabin + Roof: 4,5 t
Roof: Liquid sheath / slated sheath
Cabin body: RAL 6005 / RAL 9005
Roof: RAL 7001
BT picture holder frame
Door with two doors in fiberglass
2 Ventilation grids in fiberglass